Technical Property Operation Consulting
for Resort Development, Lodging Properties, Healthcare, Office Buildings, and Residential High-rise Buildings|
Project Name: xxxxxx Company Name: xxxxxx
Inspection Date: 03/13/xxxx Report Date: 3/22/xxxx
EXECUTIVE SUMMARY: Comments and recommendations in this report are based on the assumption that the building at some point in time will be operated as a 475+ room hotel.
Non compliance with Local Law #16 (NYC) both for fire alarms and sprinkler coverage.
Lack of front office and related areas, suggestions are given in the appropriate sections.
Lack of telephone switch for hotel use.
This building has all the potential for 3-4 Diamond hotel operation. The only concern would be the width of the corridors. The size and layout of the rooms could easily compete at the 4 Diamond level, provided the appropriate FF&E package is chosen and the area continues to improve. The zoning for this building should be further investigated.
For a complete acquisition/property inspection report or
to hear of our other programs and operation procedures please contact us.
E-Mail: firstname.lastname@example.org | Tel: (516) 782-7280 | ©2006 Craanen Technical Services, LLC